(a) Conduct initial, daily, quarterly, and annual evaluations of your continuous emission
monitoring systems that measure oxygen (or carbon dioxide), sulfur dioxide, nitrogen
oxides (Class I municipal waste combustion units only), and carbon monoxide.
(b) Complete your initial evaluation of the continuous emission monitoring systems within
180 days after your final compliance date.
(c) For initial and annual evaluations, collect data concurrently (or within 30 to 60
minutes) using your oxygen (or carbon dioxide) continuous emission monitoring system,
your sulfur dioxide, nitrogen oxides, or carbon monoxide continuous emission monitoring
systems, as appropriate, and the appropriate test methods specified in table 6 of
this subpart. Collect the data during each initial and annual evaluation of your continuous emission
monitoring systems following the applicable performance specifications in appendix
B of this part. Table 7 of this subpart shows the performance specifications that apply to each
continuous emission monitoring system.
(d) Follow the quality assurance procedures in Procedure 1 of appendix F of this part
for each continuous emission monitoring system. The procedures include daily calibration drift and quarterly accuracy determinations.
FindLaw Codes may not reflect the most recent version of the law in your jurisdiction. Please verify the status of the code you are researching with the state legislature or via Westlaw before relying on it for your legal needs.
Was this helpful?
Response sent, thank you
Welcome to FindLaw's Cases & Codes
A free source of state and federal court opinions, state laws, and the United States Code. For more information about the legal concepts addressed by these cases and statutes, visit FindLaw's Learn About the Law.