Code of Federal Regulations Title 30. Mineral Resources § 30.75.1101–7 Installation of water sprinkler systems; requirements
Search Code of Federal Regulations
Search by Keyword or Citation
(a) The fire-control components of each water sprinkler system shall be installed, as far as practicable in accordance with the recommendations set forth in National Fire Protection Association 1968–69 edition, Code No. 13, “Installation of Sprinkler Systems” and such systems' components shall be of a type approved by the Underwriters' Laboratories, Inc., Factory Mutual Research Corp.
(b) Each sprinkler system shall provide protection for the motor drive belt takeup, electrical controls, gear reducing unit, and the 50 feet of fire-resistant belt, or 150 feet of nonfire-resistant belt adjacent to the belt drive.
(c) The components of each water sprinkler system shall be located so as to minimize the possibility of damage by roof fall or by the moving belt and its load.
Cite this article: FindLaw.com - Code of Federal Regulations Title 30. Mineral Resources § 30.75.1101–7 Installation of water sprinkler systems; requirements - last updated October 02, 2022 | https://codes.findlaw.com/cfr/title-30-mineral-resources/cfr-sect-30-75-1101-7/
Was this helpful?