Welcome to FindLaw's Cases & Codes, a free source of state and federal court opinions, state laws, and the United States Code. For more information about the legal concepts addressed by these cases and statutes, visit FindLaw's Learn About the Law.
(a) All piping, valves and fittings shall meet the applicable requirements of Subchapter F (Marine Engineering) of this chapter.
(b) Distribution piping shall be of materials resistant to corrosion, except that steel or iron pipe may be used if inside corrosion resistant coatings which will not flake off and clog the nozzles are applied. Materials readily rendered ineffective by heat of a fire shall not be used. The piping shall be subject to approval for each installation.
(c) All piping, valves, and fittings shall be securely supported, and where necessary, protected against injury.
(d) Drains, strainers, and dirt traps shall be fitted where necessary to prevent the accumulation of dirt or moisture.
(e) Threaded joints shall be metal to metal, with no thread compound used.
(f) Distribution piping shall be used for no other purpose.
(g) All piping shall be thoroughly cleaned and flushed before installation of the water spray nozzles.
Cite this article: FindLaw.com - Code of Federal Regulations Title 46. Shipping § 46.34.25–15 Piping—T/ALL - last updated October 03, 2022 | https://codes.findlaw.com/cfr/title-46-shipping/cfr-sect-46-34-25-15.html
FindLaw Codes may not reflect the most recent version of the law in your jurisdiction. Please verify the status of the code you are researching with the state legislature or via Westlaw before relying on it for your legal needs.
Was this helpful?